Gas valves for use in 24 Vac, gas-fired, standing pilot appliances with capacities from 20 to 200 cfh.
- Gas valves include manual valve, two automatic operators, servo pressure regulator and pilot adjustment.
- Compact size.
- Provide two automatic valves.
- Solenoid-operated first automatic valve opens on thermostat call for heat; closes when call for heat ends.
- Diaphragm-operated second automatic valve opens under control of regulator; closes if gas or power supply is interrupted.
- Meet codes requiring dual safety shutoff.
- Natural to LP and LP to Natural conversion kits available for standard and slow opening gas valves.
- LITE-RITE (OFF-PILOT-ON) lighting sequence.
- All adjustments, wiring connections and pilot outlet are accessible from top of control.
- Adjustable servo regulator effectively maintains almost constant gas output pressure under wide fluctuations in gas supply pressure.
- Compatible with ECO connector.
ApplicationSingle StageDimensions (in.)5 3/8 in. high x 4 1/16 in. wide x 2 11/16 in. deepDimensions (mm)135 mm high x 104 mm wide x 69 mm deepIncludesOne 3/4" straight flange; One 1/2" x 3/8" reducer bushings; Natural to LP Conversion KitItem TypeProductMounting0 to 90 degrees in any direction from the upright position of the gas control knob, including vertically.Frequency60 HzApprovals, Underwriters Laboratories Inc.UL Component Recognized MCCZ2.MH5323Approvals, CSACSA International: 112395Electrical Connections1/4 in. quick-connect male terminalsVoltage24 VacOperating Temperature Range (F)0 F to 175 FOperating Temperature Range (C)-18 C to +79 CBody PatternStraight-throughOpening CharacteristicsSlowPressure Ratings (psi)1/2 psiPressure Ratings (kPa)3.5 kPaInlet/Outlet Size (in.)1/2 in. x 1/2 in.Pilot Gas OutletCompression fitting for 1/4 in. OD tubingPressure Tapping1/8 in. NPT with plugType of FuelNatural (LP with included conversion kit)Capacity (kBtuh)At 1 in. wc p.d.-- 130,000 BTUh: 20,000 BTUh minimum: 200,000 BTUh maximum Natural GasApprovals, Australian Gas Association4752Pressure RegulatorSlowPressure Regulator Setpoint (in. wc)3.5 in. WCPressure Regulator Setpoint (kPa)0.87 kPaIgnition TypeStanding PilotAnticipator Setting