Gas valves for use in 24 Vac, gas-fired, intermittent pilot appliances with capacities from 20 to 200 cfh.
- Gas valves include manual valve, two automatic operators, servo pressure regulator and pilot adjustment.
- Use with S86F,H; S8600F,H and S8610 Control Modules.
- Compact size.
- Provide two automatic valves.
- Solenoid operated first automatic valve opens on thermostat call for heat; closes when call for heat ends.
- Diaphragm operated second automatic valve opens under control of regulator; closes if gas or power supply is interrupted.
- Meet codes requiring dual safety shutoff.
- Natural to LP and LP to Natural conversion kits available for standard and slow opening gas valves.
- All adjustments and wiring connections are accessible from top of control.
- ON-OFF lighting sequence.
- Compatible with ECO connector.
ApplicationSingle StageDimensions (in.)4 5/8 in. high x 4 1/8 in. wide x 2 11/16 in. deepDimensions (mm)117 mm high x 104 mm wide x 69 mm deepIncludesNatural to LP Conversion Kit; One 1/2" x 3/8" reducer bushing; One 3/4" straight flangeItem TypeProductMounting0 to 90 degrees in any direction from the upright position of the gas control knob, including vertically.Frequency60 HzApprovals, Underwriters Laboratories Inc.UL Component Recognized MCCZ2.MH5323Approvals, CSACSA International: 112395Tradeline ValueElectrical Connections1/4 in. quick-connect male terminalsVoltage24 VacOperating Temperature Range (F)0 F to 175 FOperating Temperature Range (C)-18 C to +79 CApprovals, Canadian Gas AssociationBody PatternStraight-throughOpening CharacteristicsStandardPressure Ratings (psi)1/2 psiPressure Ratings (kPa)3.5 kPaInlet/Outlet Size (in.)1/2 in. x 1/2 in.Pilot Gas OutletCompression fitting for 1/4 in. OD tubingPressure Tapping1/8 in. NPT with plugApprovals, American Gas AssociationType of FuelNatural (LP with included conversion kit)Capacity (kBtuh)At 1 in. wc p.d.-- 150,000 BTUh: 20,000 BTUh minimum: 200,000 BTUh maximum Natural GasApprovals, Australian Gas Association4752Pressure RegulatorStandardPressure Regulator Setpoint (in. wc)3.5 in. wcPressure Regulator Setpoint (kPa)0.87 kPaIgnition TypeIntermittent PilotAnticipator Setting