Single Stage, 24 Vac, Slow Opening, Standing Pilot Gas Valve. 3/4 x 3/4". Set 3.5" WC
Gas valve for use in 24 Vac, gas-fired, standing pilot appliances with capacities from 30 to 300 cfh.
Gas valves include safety shutoff, manual valve, two automatic operators, pressure regulator and pilot adjustment.
Provide two automatic valves.
Solenoid operated first automatic valve opens on thermostat call for heat; closes when call for heat ends.
Diaphragm-operated second automatic valve opens under control of regulator; closes if gas or power supply is interrupted.
Meets codes requiring dual safety shutoff.
Natural to LP and LP to Natural conversion kits available for standard and slow opening gas valves, not for step opening gas valves.
All adjustments, wiring connections and pilot outlet are accessible from top of control.
Adjustable servo regulator effectively maintains almost constant gas output pressure under wide fluctuations in gas supply pressure.
Compatible with ECO connector.
LITE-RITE (OFF-PILOT-ON) lighting sequence.
ApplicationSingle StageDimensions (in.)5 3/8 in. high x 4 1/16 in. wide x 2 11/16 in. deepDimensions (mm)135 mm high x 104 mm wide x 69 mm deepItem TypeProductMounting0 to 90 degrees in any direction from the upright position of the gas control knob, including vertically.Frequency60 HzApprovals, Underwriters Laboratories Inc.UL Component Recognized MCCZ2.MH5323Approvals, CSACSA International: 112395Electrical Connections1/4 in. quick-connect male terminalsVoltage24 VacOperating Temperature Range (F)0 F to 175 FOperating Temperature Range (C)-18 C to +79 CBody PatternStraight-through with flangeOpening CharacteristicsSlowPressure Ratings (psi)1/2 psiPressure Ratings (kPa)3.5 kPaInlet/Outlet Size (in.)3/4 in. x 3/4 in.Pilot Gas OutletCompression fitting for 1/4 in. OD tubingPressure Tapping1/8 in. NPT with plugType of FuelNaturalCapacity (kBtuh)At 1 in. wc p.d.-- 200,000 BTUh: 30,000 BTUh minimum: 300,000 BTUh maximum Natural GasApprovals, Australian Gas Association4717Pressure RegulatorSlowPressure Regulator Setpoint (in. wc)3.5 in. WCPressure Regulator Setpoint (kPa)0.87 kPaIgnition Type Standing Pilot Anticipator Setting